This page requires frames. Please call 510-794-5520 for assistance.
Are you Interested in learning how Cleco received 1% performance recovery, 0.5% heat rate recovery and an ROI in less than six months with GTE's Multi-Stage Compressor Cleaning System?? Please review the documented case study below to find out.
Cleco Evangeline, an intermediate load following power plant, is located in rural, central Louisiana and is the Siemens LTP SGT6-5000F (W501F) class engine operational hours fleet leader. The engines experience compressor fouling from seasonal, environmental and agricultural conditions, such as pollen and prescribed burning of local sugarcane and cotton fields, resulting in loss performance. Cleco has three combined cycle SGT6-5000F engines. All three engines burn natural gas and are only used for power production. The engines run heavily during peak seasons and are generally shutdown at night. Cleco experiences intermittent LFD issues with the OEM wash system. Therefore, on-line washing is performed prior to shutdowns or during non-peak hours for risk mitigation of potential penalties. On-crank washes are performed during scheduled outages. Prior to GTE's involvement, Cleco used the OEM supplied gas turbine compressor water wash system for on-line and on-crank washing on all of their engines.
GTE started a rigorous R&D program with Cleco that encompassed a two year testing period. GTE obtained on-line and on-crank nozzle spray patterns for different nozzle sets, engine performance data, system reliability data and operator feedback, for an optimized design. The GTE test system was specifically installed on unit 7-1, which is part of the 2-on-1 power block. Cleco evenly splits the loads between the engines. Side by side performance testing techniques were used to collect data between the GTE and OEM supplied water wash systems. Performance data could be accurately corrected as measurement uncertainty was minimized.
GTE designed a patent pending, fully automated, multi-stage nozzle cleaning system for on-line and on-crank compressor water wash. The automatic on-line wash cleaning system offered full inlet throat coverage and optimized blade wetting for normalized engine loads from 60 - 100% providing operational flexibility. The system incorporated GTE's patented water wash technology and seamlessly integrated into the Siemens WDPF control system to promote regular on-line washing, by the operators. The engine received a dedicated wash system due to the operational constraints of washing prior to shutdown. The semi-automatic on-crank water wash process reduced operator involvement and decreased turbine downtime. Operator involvement would only be required to open drain valves, initiate the wash, and determine adequate engine rinsing.
Daily use of the on-line wash has cut the engine power degradation rate in half. In comparison to the OEM water wash system, the GTE system demonstrates an average percent power benefit of 1.18 % and an average increase in engine efficiency by 0.42 % over a four month span, between on-crank water washes. The on-crank wash provides improved degradation recovery above and beyond the OEM water wash system. This is primarily due to complete intake coverage, heated and highly atomized water and precision controlled injection of the OEM approved additive. Mike Bishoff, the Cleco O&M Supervisor, found the system valuable because it was an easy to use, low maintenance system that maintains power output, reduces fuel and parts cost, and has added operational flexibility. The Evangeline Power Station plans to install this system on their other two SGT6-5000F engines. The patent pending multi-stage nozzle cleaning system is commercially available to all SGT6-5000F customers directly through GTE. Similar systems are available for most industrial gas turbines.
If you are interested in learning how GTE's compressor wash system can benefit you at your plant, please contact me at anytime.
Director: Marketing and Communications
Gas Turbine Efficiency
D 407.304.5236 F 407.304.5201 M 864.356.3676 E firstname.lastname@example.org
A 300 Sunport Lane Orlando, FL 32809 W http://www.gtefficiency.com
Please consider the environment before printing this email.
Hostmaster, please convert this message to a live link to my web site,
http://www.GTEfficiency.com/, in the Advertise Forum archive.
The information transmitted is intended only for the person or entity to which it is addressed and may contain confidential and/or privileged material. Any review, retransmission, dissemination or other use of, or taking of any action in reliance upon, this information by persons or entities other than the intended recipient is prohibited. If you received this in error, please contact the sender and delete the material from any computer.
E-mail communication may be vulnerable to occurrences such as viruses, unauthorized amendment, unauthorized monitoring, tampering and data corruption. We correspond via e-mail subject to the condition that we are not liable for any such viruses, unauthorized amendments, unauthorized monitoring, tampering and/or data corruption or any consequences thereof.
501F HOME PAGE
Use the black navigation bar with white text to access the drop down
menus to manuver around the site.
This document contains proprietary information of the author and may
not be used for purposes other than that for which it was originally
furnished except with written permission of the author.
Continuing to utilize this Users-Groups.com site affirms your acceptance
of the policy specified at http://www.Users-Groups.com/policy/.